Siemens TIA Portal
ICSA： ICS Advisory (ICSA-20-014-05)
1. EXECUTIVE SUMMARY
- CVSS v3 7.8
- ATTENTION: Low skill level to exploit
- Vendor: Siemens
- Equipment: TIA Portal
- Vulnerability: Path Traversal
2. RISK EVALUATION
Successful exploitation of this vulnerability could allow a local attacker to execute arbitrary code with SYSTEM privileges.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of TIA Portal, the Totally Integrated Automation Portal, are affected:
- TIA Portal v14: All versions
- TIA Portal v15: All versions prior to v15.1 Upd 4
- TIA Portal v16: All versions
3.2 VULNERABILITY OVERVIEW
Changing the contents of a configuration file could allow an attacker to execute arbitrary code with SYSTEM privileges. This vulnerability could be exploited by an attacker with a valid account and limited access rights on the system. No user interaction is required.
- CRITICAL INFRASTRUCTURE SECTORS: Chemical, Critical Manufacturing, Energy, Food and Agriculture, Water and Wastewater Systems
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Germany
\William Knowles from Applied Risk reported this vulnerability to Siemens.
Siemens recommends installing the following software update to address this vulnerability:
- TIA Portal V15: Update to v15.1 Upd 4
Siemens has identified the following specific workarounds and mitigations users can apply to reduce the risk:
- Remove write permissions for every non-administrative user on files and folders located below the “TraceEngine” folder (usually located at “C:\ProgramData\Siemens\Automation”).
As a general security measure, Siemens strongly recommends users protect network access to devices with appropriate mechanisms. In order to operate the devices in a protected IT environment, Siemens recommends users configure the environment according to Siemens’ operational guidelines for Industrial Security, and follow the recommendations in the product manuals.
Additional information on industrial security by Siemens can be found at: https://www.siemens.com/industrialsecurity
For more information on this vulnerability and more detailed mitigation instructions, please see Siemens security advisory SSA-629512
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability. This vulnerability is not exploitable remotely.